Generally speaking, the grounding rod mainly comprises several parts, a main body of a cylindrical grounding rod, and at the upper end of the grounding rod, there is a through hole connected to the cavity, and the hole is provided with a lead wire, a connecting pipe and A supply tube. Of course, if the installer connects the ground rods together, the grounding resistance can be as low as possible. Since the ground rod has such a complicated structure and plays an important role, what is the correct way to use the ground rod?
Firstly, the hole of ф155mmX3155mm vertical ground should be drilled in the selected construction site. Secondly, 50 kg of fresh water should be placed in the container with the volume larger than 150L, the initiator should be added, stirred until all dissolved, and the synergistic ionic filler is added and stirred. To the paste, with the filler; again, disassemble the sealing tape at both ends of the grounding electrode, fill the hole in the bottom of the hole into the hole according to the filler prepared in 1:4, the top of the grounding pole is parallel to the ground plane; Lead the line, fill the remaining filler around the grounding pole to the top of the grounding pole 100mm, implant the grounding pole, cover the protective cap, measure the grounding resistance, fill the protective cap around with the soil, the top of the cap is 100mm above the ground. . Use electrolytic ion grounding rods to pay attention to strategies so that they can do their work without time and effort.