The grounding wire is divided into a portable short-circuit grounding wire and a personal security grounding wire.
The portable short-circuit grounding wire is divided into two types: combined type and split type.
High voltage grounding wire combined grounding wire
The number of clamps and the length of the grounding wire are different due to different voltage levels. A set of "grounding wires" consists of wire end clamps, operating levers, shorting wires, grounding wires, and grounding wire clamps or grounding poles. When using, first check the power, confirm that the grounding terminal clamp is fastened to the grounding pole after the power failure, and hang the wire end clamps on the wires and clamp them. When removing, first remove the wire end clamp and then remove the ground clamp. (In general, most of the three-phase electricity)
High voltage grounding line split phase grounding line
Each set of three groups. Each group is connected by a wire end clamp, a short wire and a ground wire clamp. When using the group to operate, the power should be checked first. After confirming that the power has been cut off, first fix the grounding terminal clamp on the grounding pole (or the tower), then press the power-off line voltage level, select the operating lever, and hang the wire end clamp. Clamp on the wire. After the work is completed, the wire end clamp should be removed first, and then the ground end clamp should be removed.